- About Us
- Consulting & Services
- EMF/EMI Overview
- Project Portfolio
- Contact Us
Virtually all commercial buildings have areas with elevated AC (60 Hz – power frequency) magnetic fields which can cause interference problems with sensitive electronic equipment, and may be of possible health concern when continuously occupied. These are unavoidable; they are caused by electrical distribution equipment such as transformers, distribution switchboards, distribution service panels, and distribution electrical feeders/conduits. Most commercial buildings have background fields in the range of 2-4 milliGauss, but also have areas containing “hotspots” with much higher readings near these current sources. With today’s increasingly sensitive electronic technology, even relatively low background fields may be sufficient to cause equipment interference.
Problems with AC (60 Hz – power frequency) magnetic fields frequently emerge immediately after a new tenant moves in or after a build out or renovation. Space that was either previously unused or not used for sensitive electronic equipment operations may suddenly develop a problem. For example, a previous “low tech” tenant may not have used computers extensively, but a new high-tech tenant has sensitive data communications and processing equipment that is sensitive to interference from AC (60 Hz – power frequency) magnetic fields as low as 2 to 3 mG.
New EMI problems are also common when there is a change in the building’s power structure. Proper planning during a renovation or lease negotiation can save considerable time and money if there is a potential EMF problem.
FMS was engaged as the project’s EMI Consultant to conduct an AC (60 Hz) electromagnetic field (EMF) assessment of the existing transmission corridor located in Mission Viejo, CA.
FMS was engaged as the project’s EMI Consultant to site and house a Transmission Electron Microscope (TEM)
WVUE-FOX 8 – Benson Tower is a 5,800 square foot studio project designed by Eskew+Dumez+Ripple.
Over its 20 years, FMS has successfully completed hundreds of EMI projects which included a diverse range of consulting and mitigation services.